|Vendor||Equipment Name||Leak Rate / Threshold / Max Tank Capacity|
|AC’CENT Environmental||Dri-Sump Containment Tightness Test Method||0.1 gph with PD = 100%, and PFA = 0%|
|Franklin Fueling Systems||Incon TS-STS Sump Test System||0.00192 inch in 15 minutes with PD=95%/0.0080 inch/hr|
|Fueling and Service Technologies, Inc.||Hydro-Tite™ Leak Detection System For Secondary Containment||0.00065 inch in 12 minutes with PD = 95%/0.010 inch/hour|
|Leak Detection Technologies, LLC||DPleak Differential Pressure Leak Test – Leak Detection and Leak Location Test Method||0.1 gph with PD = 100%, and PFA = 0%.
0.005 gph with PD = 96%, and PFA = 0%
|MCleak Enhanced Interstice Test for Doubled-Walled Tanks, UDCs, Sumps and Spill Buckets||Leak Rate – 0.005 gph w/ 72 hour wait before testing/1,500 interstitial capacity. Leak Threshold – 0.0017 gph|